TSWA Type Horizontal Multi-stage Centrifugal Pump/Horizontal multi-stage centrifugal pump has the characteristics of high efficiency, wide performance range, safe and stable operation, low noise, long life, convenient installation and maintenance, etc. For transporting clean water or other liquids with physical and chemical properties similar to water. Mainly suitable for urban high-rise building water supply and drainage and fire fighting water, factory, mine water supply and drainage, long-distance water delivery, production process cycle water, HVAC cycle, domestic water and other purposes.
Installation matters editing Voice
1. The weight of the pipeline should not be borne on the pump during installation, otherwise the pump will be easily damaged;
2. The anchor bolts must be tightened during installation, and the pump should be inspected every certain period of time to prevent it from loosening, so as to avoid severe vibration when the pump is started and affect the performance of the pump;
3. Before installing the water pump, carefully check whether there are any hard objects (such as rocks, iron sand, etc.) that affect the operation of the pump in the pump flow path to avoid damaging the flow parts during the operation of the pump:
4. For easy maintenance and safe use, install a regulating valve on the inlet and outlet pipelines of the pump and a pressure gauge near the inlet and outlet of the pump. For high-lift pumps, to prevent water hammer, it should be installed before the outlet gate valve. A check valve to deal with accidents caused by power loss such as sudden power failure, so as to ensure that the pump runs under the best working conditions and prolong the service life of the pump;
5. When the pump is used for suction lift occasions, it should be equipped with a bottom valve, and the inlet pipeline should not have too many bends, and there should be no water leakage or air leakage, so as not to affect the suction performance of the pump;
6. In order to prevent impurities from entering the pump and clogging the flow path to affect performance, a filter should be installed in front of the pump inlet;
7. Rotate the rotor parts of the water pump before installing the pipeline. There should be no friction or jamming. Otherwise, the pump should be disassembled to check the cause.
Hot Tags: TSWA Type Horizontal Multi-stage Centrifugal Pump, China, Manufacturers, Suppliers, Factory, Wholesale, Price